TCSB5406W wireless manual call point is suitable for installation in public places, factories and other environments. When a fire is manually confirmed, press the button, and the red light of the MCP is always on, so that an alarm signal can be sent to the control panel through wireless communication technology. When the control panel responds to the
alarm signal, the MCP enters a state of waiting for the control panel to reset, and the control panel displays the coded information of the MCP and gives an alarm sound.
All data is supplied subject to change without notice.
Specifications are typical at 24V, 25℃ and 50% RH unless otherwise stated.
Battery CR17450 3V
Voltage range 2.7~3.3V
Operating current monitoring current≤10uA , alarm current≤19mA
Coding method automatically assigned when networking Radio frequency transmit power<20dBm
Frequency band 470MHz
Operating environment temperature 10℃~+55℃
relative humidity ≤95%
Push-type structure design is adopted, and special tools are required to reset after
pressing MCP; Using 470MHz wireless communication technology, there is no need to embed wiring, and the engineering installation is convenient and fast; with battery low voltage detection function, which can reflect the battery power situation in time; Using microprocessor to realize signal processing, communicating with controller by digital signal, it works stably and reliably, and has good ability to suppress electromagnetic interference.