DC24V LPCB Approved Addressable fire alarm button ressetable manual fire alarm call point works with TC series addressable fire alarm system.
Installed in public places; when there is a fire, pressing
the frangible element on this MCP can send fire signal
to fire alarm control panel
Alarm by pressing, reset by a special key
Non-polarized two-wire to the control panel
Operating voltage Loop 24V(18.5V～26V)
Operating current Standby current: ≤0.2mA;Alarm current: ≤0.8mA
Operating Environment Indoor Temperature: -10°C～+55°C;Relative Humidity: ≤95%, non-condensing
Indicator Red. Flashes about every 3s when polling;Illuminates after in alarm
Coding method Electronically coding
Code range 1～255
Material and color of enclosure ABS; Red
Weight About 120g (with base)
Mounting hole distance 60mm
Dimension (L×W×H) 95mm×44mm×95mm (with base)
Product installation manual and video at https://www.vedard.com/forum/tc-fire-alarm-system-manual.html
No reviews yet.
Let users know what you would have wanted to know about this company.